Zhejiang Chinatide Solar & Luminous Energy Co.,Ltd
Add: No.28 Minfeng Road,Minfeng Industrial Park of Yuanhua Town, Haining City
Ben Shi: shreklove312.
Alice Yin: siberian0318
Jacky Guo: firstname.lastname@example.org
Julia Zhang: email@example.com
Amy Liu: firstname.lastname@example.org
Bella Li: email@example.com
Lisa Yang: firstname.lastname@example.org
Zero Cai: email@example.com
Viny Tian: firstname.lastname@example.org
Non-pressure Solar Water Heater With Assistance Tank
Working Principle： This type is same as CT-NP01, using all-glasses evacuated tubes as the solar collector for absorbing sun energy and transferring it into heat energy. As the different densities of hot water and cold water, the hot water flows automatically upwards while the cold water flows...
This type is same as CT-NP01, using all-glasses evacuated tubes as the solar collector for absorbing sun energy and transferring it into heat energy. As the different densities of hot water and cold water, the hot water flows automatically upwards while the cold water flows down. The water flowing cycle is created in the tube. And the water in the storage tank is heated from this natural circulation. The hot water pressure of this non-pressure system is from the gravity, so it should be installed on the roof or at least 3-4 meters higher than hot water tap. Or you can install a booster pump to get stronger outlet hot water.
The only difference is that CT-NP01 is with an assistant tank and CT-NP02 is without.
20GP/40HQ Loading Qty(sets)
Inner tank: SUS 304-2B/0.41mm, Φ360mm
Outer tank: Galvanized steel/0.41mm, Φ460mm
Insulation Layer: high density polyurethane foam 50mm
Vacuum tube: 58*1800mm/SS-CU-AIN/ALN or AL-N-AL coating
Bracket: Galvanized steel 1.5mm with 20/25/38/45/50 degree installing angle.
Electrical heating connection(inch): ¾ or 1¼
Water connection(inch):½ or ¾
NOTE: All the systems are available for the customization.
1.Booster Pump (adding the hot water out pressure)
2.Temperature Monitor (showing hot water temperature inside the main tank)
3.Electrical Heater (as back-up for cloudy or rainy day)